Click Here for a Carlon HDPE Quote Request
Applications: Underground (direct bury), or placed inside existing duct (innerduct). Ideal for use in parking lots, traffic lights, etc.
Installation methods: Plowing, open/ continuous trench, directional boring or pulled through existing conduit.
ETL Listed HDPEis a nonmetallic flexible raceway manufactured from High Density Polyethylene (HDPE), offering a protective pathway for cables and wires, and is used in underground or innerduct applications. ETL Listed HDPE conduit is compliant with the NEC Articles 300 and 353, and is listed to UL 651 A & B. Its high tensile strength-to-weight ratio, superior crush resistance, and low coefficient of friction when installing cable makes it ideal for directional boring.
*Refer to UL 651B standards/ specifications for dimensional requirements.
ETL Listed Options
Schedule 40 1" 4"
Schedule 80 2" 6"
EPEC-B (SDR 13.5) 2" 6"
Multiple colors and stripes
Sequentially marked footage
Available in smoothwall only
Conforms to NEMA TC-7 Smoothwall Coilable PE Electrical Plastic Conduit
1.1Carlon HDPE duct is manufactured to the following various industry standards and specifications for dimensional requirements.
UL 651A Type EB and A Rigid PVC Conduit and HDPE conduit.
UL 651B Continuous Length HDPE.
ASTM F 2160 Solid Wall High Density Polyethylene (HDPE) Conduit Based on Controlled Outside Diameter (OD).
ASTM D 3035 Polyethylene (PE) Plastic Pipe (SDR) Based on Controlled Outside Diameter.
NEMA TC-7 Smooth Wall Coilable Polyethylene Electrical Plastic Conduit.
Carlon duct is manufactured from a suitable thermoplastic polymer conforming to the minimum standard of PE334420E/C as defined in ASTM D3350.
Carlon High Density Polyethyleneduct is manufactured in the following configurations: Smoothwall Smooth Interior and Smooth Exterior wall.
3.0 Product Description
Polyethylene conduit is an extruded coilable tubing for use as a single or multiple raceway. The conduit may be direct buried, encased in concrete and used as innerducts. Innerducts are used primarily to provide multiple raceways within an existing conduit system.
Conduit 3" or larger supplied on reels needs to be re-rounded as outlined in ASTM F2160.